Fıre response performance classes for building materials other than flooring
Equivalences of the fire response classes of building materials stated by the relevant eu commission decisions with the flammability classes of building materials specified in the regulation on the protection of buildings from fire with decision number 2002/4390
|Inflammability of the material||
Europe classification (According to TS EN 13501-1)
|Not Easily Combustible||A2 - s1, d0|
|B,C - s1, d0|
|A2 - s2, d0
A2, B, C - s3, d0
|A2, B,C - s1, d1
A2, B,C - s1, d2
|(minimum)||A2, B, C – s3, d2|
|Normal Flammable||D - s1, d0
D - s2, d0
D - s3, d0
|D - s1, d2
D - s2, d2
D - s3, d2
|(minimum)||E - d2|
Standards and Test Reports For Residence Pipe and Fittings
*Meets the mechanical and physical requirements of BD class of the TS EN 1329-1 standard.
BD Implementation class covers in-building and surface application areas, in-building under the surface application areas, and application areas up to the sewer connection of the building.
* Residence Pipes and Fittings are of the non-flammable class within the scope of the "Regulation on Protection of Buildings from Fire" as stated in the 2007/12937 decision of the Ministry of Public Works and Settlement.
As a result of the fire response performance test carried out at UL (Underwriters Laboratories), an independent US-based product safety certification agency, Residence Pipes and Fittings are categorized as V-0 NON-COMBUSTIBILITY class.
* TSE TEST AND CALIBRATION CENTRE EXAMINATION AND TEST REPORT Fire response classification of Residence Pipe and Fittings was found as B S2 D0 according to TS EN 13501-1 + A1: 2013-04 Fire Response Classification of Construction Products And Building Elements. Fire Class B, Smoke Formation S2, Flaming Droplets D0.
FRAUNHOFER INSTITUT FÜR BAUPHYSIK
* According to the test report "Determination of Acoustic Performance in Laboratory Conditions of Waste Water Installation Systems" by Fraunhofer IBP Institute of Building Physics, the sound value of Residence Pipe and Fittings was tested at 17 dB.
Residence Pipe Systems are soundproof.
According to the results of the sound level measurement test done at the Fraunhofer Institut Bauphysik (Germany) Residence Pipes and Fittings meet all national and international standard requirements.
|Flow Rate (liters per second)||0,5||1,0||2,0||4,0|
|Characteristic Sound Level _ Decibels (dB(A)) (Pipe clamp system)||3||8||12||17|